Introduction / Table of Contents
CDA has converted the Copper Tube Handbook into an app for either your tablet or smartphone. The new app makes it easier and quicker for plumbers, HVAC technicians and contractors to obtain information about copper tube, piping and fitting as well as different joining methods and applications. Available from the Apple App store or Google Play store, users now have this 60+ page manual available on their mobile devices whenever and wherever they need it.
Modern technology, recognizing that no material is superior to copper for conveying water, has reconfirmed it as the prime material for such purposes. Years of trouble-free service in installations here and abroad have built a new reputation for copper piping in its modern form—light, strong, corrosion resistant tube. It serves all kinds of buildings: single-family homes, high-rise apartments and industrial, commercial and office buildings.
Today, copper tube for the plumbing, heating and air-conditioning industries is available in drawn and annealed tempers (referred to in the trades as "hard" and "soft") and in a wide range of diameters and wall thicknesses. Readily available fittings serve every design application. Joints are simple, reliable and economical to make—additional reasons for selecting copper tube.
Today, nearly 5,000 years after Cheops, copper developments continue as the industry pioneers broader uses for copper tube in engineered plumbing systems for new and retrofitted residential, industrial and commercial installations.
Access the complete Copper Tube Handbook:
1. Standard Tubes
The first section of the Copper Tube Handbook describes the different types of copper tube, their properties and how to identify them. Browse
2. Selecting the Right Tube for the Job
This section highlights the advantages of copper tube and offers recommendations for various applications. Browse
3. Design and Installation Data
This section provides design and installation data for a variety of copper tube applications and uses in systems such as pressure systems, drainage, solar energy, agriculture, etc. Browse
Because of its exceptional formability, copper can be formed as desired at the job site. Copper tube, properly bent, will not collapse on the outside of the bend and will not buckle on the inside of the bend. Tests demonstrate that the bursting strength of a bent copper tube can actually be greater than it was before bending.
5. Joining Methods
There are three categories of methods to join copper tubing: Solder or Brazed Joints, No-flame Joints, and Additional Joining Methods.
6. Fittings, Solders, Fluxes
Soldered joints, with capillary fittings, are used in plumbing for water lines and for sanitary drainage. Brazed joints, with capillary fittings, are used where greater joint strength is required or where service temperatures are as high as 350°F. Brazing is preferred, and often required, for joints in refrigeration piping. Browse
7. Soldered Joints
The American Welding Society defines soldering as "a group of joining processes that produce coalescence of materials by heating them to a soldering temperature and by using a filler metal (solder) having a liquidus not exceeding 840°F and below the solidus of the base metals." In actual practice, most soldering is done at temperatures from about 350°F to 600°F. Browse
8. Brazed Joints
Strong, leak-tight brazed connections for copper tube may be made by brazing with filler metals which melt at temperatures in the range between 1100° F and 1500° F. Brazing filler metals are sometimes referred to as "hard solders" or "silver solders." These confusing terms should be avoided. Browse
9. Flared Joints
While copper tube is usually joined by soldering or brazing, there are times when a mechanical joint may be required or preferred. Flared fittings are an alternative when the use of an open flame is either not desired or impractical.
10. Roll Groove Joints
Grooved-end piping has been familiar to pipe fitters and sprinkler system contractors for many years. Since 1925, this method of joining pipe has been used reliably on steel and iron pipe in HVAC, fire protection, process piping and related applications. Browse
11. Press-connect Joints
Press-connect joining of copper and copper alloy tube is fast, economical, and, most importantly, it requires no heat or open flame unlike soldering or brazing. Browse
12. Push-connect Joints
Like the press-connect joining method, the push-connect joining of copper and copper alloy tube is fast, economical and, also, requires no heat or open flame. Browse
13. Mechanically Formed Extruded Outlets
Another joining technology that has been used effectively for many years involves a hand tool designed to quickly pull tee connections and outlets from the run of the tube, thus reducing the number of tee fittings and soldered or brazed joints. Browse
14. Technical Data
Index of Tables and Figures that represent the supporting technical data.